Installation of Electrical Pipes
Installation of Electrical Pipes
At first, after the project controls in accordance with the regulation, the locations and dimensions of the cases, junction boxes and sockets are determined. It can be of an apartment, an office, a shop or a hotel room.
Taking the necessary materials into our hands; First meter, laser scales in sensitive places, coil pipe, spiral pipe, fastening apparatus such as stainless construction wire, spirit level, junction box, casing, pipe, hammer for breaking and wall breaking, various cutting machines for cutting in aerated concrete, briquette, brick available. It opens channels for pipes. On the link: https://www.hilti.com.tr/c/CLS_POWER_TOOLS_7124/CLS_DIAMOND_CUTTING_SLITTING_TOOLS_7124/CLS_ELECTRIC_CUTTERS_7124/r3941?itemCode=47994
Sıva altı montajda boruları dikey olarak indirmemiz bir kuraldır. Aksi sipariş edilmedikçe, borulama yapmayın ve mümkün olduğunca az dirsek kullanın. Use elbows in sharp places and situations because if normal coil pipe is used, it will break and crush the pipe. At the same time, do not give your pipes very sharp S turns as you can, you will have difficulty in workmanship.
After the walls in accordance with the project are started to be built, the markings are started for the crushing, cutting and placing of the case, taking into account the sensitivity of the work and preparing the necessary tools and electrical tools.
According to the project, after the marking, cutting and crate layout are completed (when the crate is placed, the casing should not be buried too deeply in wet areas and on uneven walls and where it is located. In these cases, we need to learn the size of the casings we call plaster share and leave a share according to the size. Be sure to take this into account and the problem is, crates are usually attached with plaster and tile grout) Then the pipes begin to be placed for the laying process.
According to the project, junction boxes are not used much in 2021, except for some apartments. In systems with junction boxes, distribution can be made to 5 different cases, with a maximum of 5 sockets from the fuse box to the junction box.
It comes with a main line and 5 separate sockets can be added and cable can be pulled. At the same time, the cables coming from the lighting and the lighting switch can come and connect to the junction.
This system is old system. However, in systems without junction boxes, how many sockets are to be fed from a line, the cable goes to the first casing and then the pipe is laid from the casing to the casing.
The reason why I explain this cabling system is that the project shows the cable drawing, so the pipes are laid according to the cables. In other words, when you start the cable laying while laying the empty pipe, the question marks in your mind will disappear.
The fuse box, which is attached before the pipes, goes from the panel, junction box to the cases or it can go to the ceiling lighting, as well as the lighting on the wall, on the mirror. Piping, pipe laying can be considered within the framework of this plan.
In order to fix the pipes to the wall, we drill small holes on the right and left of the pipe and thread around it and fix it. Ask the fixing system to the master or formen responsible for you, we need to make the breaking or cutting process too deep or wide outside the pipe diameter.
Our recommendation is to first drill your electrical casings with a 7 cm hss drill, expand it, place your case at the appropriate height for the project, and then fix it with plaster or mortar.
Note: Before laying the boxes, it will be more practical to determine and drill how many pipes will enter in which direction on the floor. It is made by placing mortar according to the direction of the pipe. When fixing the cases, you should definitely pay attention to the size and balance. Especially for those who are in groups of two, three and four, which we call a group.
The first step is to install the casings and fuse box, junction box or panel, and then start laying from these points to the casings or lighting ends according to the project.
After your cases, junction boxes and piping are finished, you need to place the case covers and junction box covers, otherwise, when the plaster or plaster operations are started, the inside of the cases and junction boxes will be filled. If the close is not available, you can jam the paper instead of the old-fashioned cover.
My second note: we must never start by rote. Numerous types of fuse boxes, junction boxes and safes are available in this 21st century. For this reason, the products used in each project differ. First, examine the project well, ask about the product to be used, consider the assembly instructions.
- Coiled pipe (can be 20, 22, 25 or 32)
- Steel wire
- Crochet to attach to the ceiling
- Supplement mus
- Sprial pipe
- Different fastening products are also available.
At the same time, there is a piping system that we call surface mounted. Not all piping systems are made of plaster. Depending on the project; we see it in some offices, shops, parking lots, electrical facilities and even homes in the new era. Since the products of this system differ, you should definitely ask before applying. You have to be very careful about workmanship and symmetry in this kind of work. Unlike flush mounting plumbing, make sure you mark it beforehand and then start drilling holes.
There are different fixing apparatuses in surface installation, it differs according to aesthetics and durability. At the same time, the used junction boxes and other materials are also taken as surface-mounted and used. There is no case in surface mounting, the products used are suitable sockets, switches and lighting products on plaster. Surface mounted projects should not start without consulting the engineer.
3) Crate filling:
5) Pipe laying (Piping):
By the way, you might be asking why there aren't more photos. Rightly, but the piping installation is not obvious in the photos. You either have to see it in action or watch the videos. Have plenty of energy.